- Case Studies
- Home Performance
- Energy Audits
- Air Sealing
- The Economics of Energy Efficiency and Renewables.
- High Efficiency Windows
- Home Certifications
- Remodeling and Energy Efficiency
- Contact Us
Neighborhood: East Bayside, Portland, ME
Square Feet: 863
Original Condition and Performance
King Pine Homes purchased this property in the summer of 2015. The house was in need of numerous energy upgrades and a whole house remodel. For example, the shingles, sheathing, and plaster walls were all deteriorated and crumbling. In addition, there was knob and tube wiring and leaky cast iron pipes. The heating system, installed in the 1970's, was in equally rough shape requiring immediate replacement.
Worse yet, insulation and air sealing were virtually non-existent. Large cracks and holes were visible to the naked eye, as the shingles had shrunken over time and the sheathing was comprised of a mishmash of old boards. With no insulation in the walls or basement, and very little in the attic, the house was tough to heat considering its small size.
The retrofit was part of a complete home renovation and remodel that required our contractors to completely gut the house down to the studs. As the home was rebuilt, the following energy upgrades were incorporated:
Removed old gas boiler, water pipes, and baseboard radiators. Installed two new mini-split heat pumps with an electric baseboard system to serve as a backup.
Removed outdated electric water heater and installed a new heat pump electric water heater (40 gallons).
Installed 2.85 kW photovoltaic solar array on the roof.
Installed new zip system sheathing and roof decking.
Sealed basement slab.
Blew in spray foam insulation along basement walls (R15).
Built double stud walls in the interior of the house to increase wall cavity depth; blew in dense-packed cellulose into wall cavities (R25).
Blew in spray foam insulation alongside rigid board insulation in attic eves; used dense-packed cellulose in slopes (R40).
Installed new ENERGYSTAR-rated windows (U factor 0.33, SHGC 0.35) and insulated fiberglass doors.
Wired in all new LED light fixtures.
Purchased new ENERGYSTAR-rated appliances.
Installed Panasonic Whisper Green bathroom exhaust fans.
Energy auditors from Rook Energy Solutions analyzed and tested the home once construction was completed. Using their thermal imaging cameras, they confirmed there was no thermal bridging throughout the building. A blower door test was done and measured 890 CFM at 50 pascal (0.28 air changes per hour), which represented an 84.5% reduction in air leakage.
The heat pumps, which serve as the primary heating and cooling source for the home, are expected to consume 3,512 kWh per hear. Domestic hot water is projected to use another 2,004 kWh, appliances 290 kWh, and lighting 285 kWh. The total anticipated electrical load for the home is 6,092 kWh per year. On the production side, the 2.85 kW solar array on the roof will generate 4,056 kWh per year, offsetting 67% of the home's consumption.
At King Pine Homes, we're interested in figuring out how much it costs to take an ordinary home and turn it into a "pretty good" home. And by this, we mean a home that is well-built, energy-efficient, comfortable, and has healthy indoor air. To figure out the price tag for this transformation, we've attempted to identify what a "base-level" remodel would cost. We then compare it with our actual retrofit costs. The figures below represent the difference between the products used in a base-level remodel and the high-performance products we used.
$15,000 - Insulation (including double stud walls);
$5,000 - Air sealing;
$1,500 - Windows and doors;
$6,400 - Mini-split heat pumps;
$1,300 - Heat pump water heater;
$350 - ENERGYSTAR appliances; and
$500 - LED light fixtures.
$30,050 - Subtotal
- $3,000 - Efficiency Maine Rebates
$27,050 - Total Cost
Estimated Payback Period: 7.1 years
Renewable Energy (Solar)
$11,400 - Upfront cost for 2.85 kW system
- $3,420 - Investment Tax Credit
Estimated Payback Period: 22.4 years